• 100% Satisfaction Guarantee
Craig, Electrical Technician
Category: Electrical
Satisfied Customers: 4529
Experience:  33 years experience electrical troubleshooting industrial equipment and control systems.
21549903
Craig is online now

# I have a 120 volt hot water heater. The hot wire draws 16

### Resolved Question:

I have a 120 volt hot water heater. The hot wire draws 16 amps and the ground is drawing 9 amps, and all both wires are hot. Why?
Submitted: 4 years ago.
Category: Electrical
Expert:  Craig replied 4 years ago.

Craig :

The water heater element is going to ground and pulling high current.

Craig :

This is the extra current that is over heating the wires. I highly recommned replacing the element immediately.

Craig :

You don't want to over heat the wiring

Craig :

You have two circuits, one is through the element and one circuit is the element to ground.

Craig :

Replace element right away.

Customer:

I replaced the element, but nothing changed.

Craig :

I want you to measure the current on this circuit at the breaker panel. First measure the hot wire from the breaker. Then measure the current on the neutral white wire. Are they equal? If not measure the ground wire for current.

Customer:

The hot wire draws 16 amps, and the neutral wire is 16 amps.

Craig :

That is normal, this should not over heat the wire, as long as it is #12 AWG. Normal reading here. Teh only thing that may have happened is loose connections in wire nuts, causing heat and melting.
That's what I suspect here.

Craig :

You old element was going to ground also because you had 9 amps on the ground wire. It cannot do this unless the element is grounding out, and current returns on the ground wire. Normal is what you see now, equal hot and neutral amps.

Customer:

I still have 9 to 16 amps on the ground wire. All wires are still hot to the touch when used. Changing the element did not change anything. I have turned it off except when needed for short periods of time.

Craig :

One of the thermostat wires is grounding then. You are going to have to use your ohm meter and trace the ground fault out. Here's how:

Craig :

Turn breaker off at panel. Then at water heater open the top box where the thermostat is. On mid range ohms setting, touch the hot black feed wire and the ground wire with leads. Should read ∞ ohms (infinite). You will see some ohms value to ground on your meter. So start isolating the black feed wire, start by unhooking the thermostat and then read ohms each way, wire to and wire into thermostat. Continue this until you see where the hot is going to ground. Also test the element to ground with it unhooked from black and white coming to heater. Just read the circuit through the heater to ground.

Craig :

Must be unhooked from white wire feeding to breaker panel or you will read a ground.

Craig :

The white neutral is grounded at panel so make sure you unhook it at water heater to do this testing.

Craig :

There is a ground inside on the element or the thermostats.

Craig, Electrical Technician
Category: Electrical
Satisfied Customers: 4529
Experience: 33 years experience electrical troubleshooting industrial equipment and control systems.

Ask-a-doc Web sites: If you've got a quick question, you can try to get an answer from sites that say they have various specialists on hand to give quick answers... Justanswer.com.
...leave nothing to chance.
Traffic on JustAnswer rose 14 percent...and had nearly 400,000 page views in 30 days...inquiries related to stress, high blood pressure, drinking and heart pain jumped 33 percent.
Tory Johnson, GMA Workplace Contributor, discusses work-from-home jobs, such as JustAnswer in which verified Experts answer people’s questions.
I will tell you that...the things you have to go through to be an Expert are quite rigorous.

### What Customers are Saying:

• You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future. Jimmy Bagley, IA
< Previous | Next >
• You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future. Jimmy Bagley, IA
• Wonderful service, prompt, efficient, and accurate. Couldn't have asked for more. I cannot thank you enough for your help. Mary C. Freshfield, Liverpool, UK
• This expert is wonderful. They truly know what they are talking about, and they actually care about you. They really helped put my nerves at ease. Thank you so much!!!! Alex Los Angeles, CA
• Thank you for all your help. It is nice to know that this service is here for people like myself, who need answers fast and are not sure who to consult. GP Hesperia, CA
• I couldn't be more satisfied! This is the site I will always come to when I need a second opinion. Justin Kernersville, NC
• Just let me say that this encounter has been entirely professional and most helpful. I liked that I could ask additional questions and get answered in a very short turn around. Esther Woodstock, NY
• Thank you so much for taking your time and knowledge to support my concerns. Not only did you answer my questions, you even took it a step further with replying with more pertinent information I needed to know. Robin Elkton, Maryland

• ### Mike

#### Satisfied Customers:

1425
Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer
< Last | Next >

### Mike

#### Satisfied Customers:

1425
Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer

### Jason

#### Satisfied Customers:

3871
Over 20 years of experience in all types of installations, troubleshooting, and repairs.

### Mike G.

#### Satisfied Customers:

6511
Proven Professional 46 years Experience

3264

### Kevin

#### Satisfied Customers:

2371
29 years as a Licensed Electrical Contractor in Illinois, 5 year college Electrical Instructor, Former Electrical Inspector, Diploma in Digital Electronics, Former Illinois Licensed Home Inspector

### electrifier

#### Satisfied Customers:

1458
Electrical contractor and electrical inspector for over 24 years with phone and networking expertise