• 100% Satisfaction Guarantee
Sir Sparks, President/Owner/ Master Electrician
Category: Electrical
Satisfied Customers: 2532
Experience:  US State Certified & UK Electrical Contractor for all electrical fields/disciplines
22778599
Sir Sparks is online now

# I am wiring a contactor to a well pump with a float switch.

### Resolved Question:

I am wiring a contactor to a well pump with a float switch. The contactor has a 120 volt coil. The pump is 240 volt. The wire to/from the pump float is 18 gauge.
Submitted: 6 years ago.
Category: Electrical
Expert:  Sir Sparks replied 6 years ago.

-Could you explain your situation a little more?

Edited by Sir Sparks on 3/26/2010 at 11:41 PM EST
Customer: replied 6 years ago.
Can you give me a diagram on how to wire this contactor?
The contactor is 120 volt but the supply and the load are 240 volt.
There is also the 18 g wire from the well float. Should I install an in-line fuse on the 18g
Expert:  Sir Sparks replied 6 years ago.

Hi, I don't do diagrams but it is so easy anyway.

240 volt feed; one wire to each side of contacts on contactor then 1 wire from each other side to pump.

Also one side of feed wires to one side of contactor with second side to float switch, finally the last wire of float switch to neutral.

No need for an inline fuse.

Customer: replied 6 years ago.
Don't I need to bypass one leg of the 240 feed since the contactor coil is 120 volt, not 240?
To make it more clear:
One leg each of 240 to L1 and L2.
A jumper from one of those legs to contacts with the other contact wired to the float switch. Second wire from float switch is wired to a neatral ground.
Then T1 and T2 to well pump.
???
Expert:  Sir Sparks replied 6 years ago.
Yes, to neutral. But not ground. That is what I said; one leg to contactor coil, other leg of coil to float, second wire of float to neutral.
Customer: replied 6 years ago.
I am confused.
My 240 is single phase, 2 lines and a ground.
What is the neutral line?
Expert:  Sir Sparks replied 6 years ago.
I see. You MUST use a neutral or change the coil to 240 volts. No choice, sorry.
Sir Sparks, President/Owner/ Master Electrician
Category: Electrical
Satisfied Customers: 2532
Experience: US State Certified & UK Electrical Contractor for all electrical fields/disciplines

Ask-a-doc Web sites: If you've got a quick question, you can try to get an answer from sites that say they have various specialists on hand to give quick answers... Justanswer.com.
...leave nothing to chance.
Traffic on JustAnswer rose 14 percent...and had nearly 400,000 page views in 30 days...inquiries related to stress, high blood pressure, drinking and heart pain jumped 33 percent.
Tory Johnson, GMA Workplace Contributor, discusses work-from-home jobs, such as JustAnswer in which verified Experts answer people’s questions.
I will tell you that...the things you have to go through to be an Expert are quite rigorous.

### What Customers are Saying:

• You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future. Jimmy Bagley, IA
< Previous | Next >
• You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future. Jimmy Bagley, IA
• Wonderful service, prompt, efficient, and accurate. Couldn't have asked for more. I cannot thank you enough for your help. Mary C. Freshfield, Liverpool, UK
• This expert is wonderful. They truly know what they are talking about, and they actually care about you. They really helped put my nerves at ease. Thank you so much!!!! Alex Los Angeles, CA
• Thank you for all your help. It is nice to know that this service is here for people like myself, who need answers fast and are not sure who to consult. GP Hesperia, CA
• I couldn't be more satisfied! This is the site I will always come to when I need a second opinion. Justin Kernersville, NC
• Just let me say that this encounter has been entirely professional and most helpful. I liked that I could ask additional questions and get answered in a very short turn around. Esther Woodstock, NY
• Thank you so much for taking your time and knowledge to support my concerns. Not only did you answer my questions, you even took it a step further with replying with more pertinent information I needed to know. Robin Elkton, Maryland

• ### Mike

#### Satisfied Customers:

1425
Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer
< Last | Next >

### Mike

#### Satisfied Customers:

1425
Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer

### Jason

#### Satisfied Customers:

3871
Over 20 years of experience in all types of installations, troubleshooting, and repairs.

### Mike G.

#### Satisfied Customers:

6511
Proven Professional 46 years Experience

3264

### Kevin

#### Satisfied Customers:

2371
29 years as a Licensed Electrical Contractor in Illinois, 5 year college Electrical Instructor, Former Electrical Inspector, Diploma in Digital Electronics, Former Illinois Licensed Home Inspector

### electrifier

#### Satisfied Customers:

1458
Electrical contractor and electrical inspector for over 24 years with phone and networking expertise