no matter what combination of breakers Main or Feeds, there is no power to the second bus.
with feed breakers and main breaker on it reads 120 to ground one leg and 0v to ground other leg. and 120 between the two power leads coming in
with main breaker on and feed breakers off there is no power bus but main breaker input reads 120 v from phase to phase coming in.
no comination of breaker will indicate 220v between the incoming power leads
the utility company does not believe that it is a feed problem
shouldn't there be 220v from phase to phase coming from the utility regardless of what is going on inside the house if that feed breaker is in the off position??