Thank you for asking your question on Just Answer!!!
You are corresponding with Joseph - Your personal On-Line “Electrical Consultant”
*****Click here to view my profile*****
You will need to borrow one then. Start with your electrical panel. You will need to take the panel cover off and test your breaker that feeds the well pump as such: If your breaker reads ok - then you need to go outside to your well and test the pressure switch. You will see a line and load side wiring. Test the line side to be sure you have the same voltage coming in as you did with your breaker. Then very carefully - use a wooden stick to push down on the contacts of the pressure switch. If your pump kicks on - then the pressure switch is the problem. You will need to replace it in order to get water.
Hope this helps you out. If you should need anything further please don't hesitate to ask. Good Luck!!
Please press the "Accept" button if my answer has helped. This is the only way I get paid for providing my services. Don't forget to leave feedback - bonuses are also welcome and appreciated!!!
100% customer satisfaction is my goal!!!
Have another electrical question?
Bookmark my profile page by adding me to your favorites.
Click Here: Contact Electric Doctor ----- A Just Answer Verified Electrical Expert!!!
Don’t forget to put “Question for Electric Doctor” in the Subject line!!!