Hi,Welcome to Just Answer, My name is XXXXX XXXXX forward to helping you today.
Can you get me the full model number it should be inside the door when you open it on a tag, thanks, Bryan
ground to each wire at element connectors w/ volt meter
didn't try that
i did tie the fuse wires together and ran dryer with no heat
should i disconnect from element to do this?
pulled one wire off and put the meter between wire and element and got 63 volts
i'm baffled because i read 10.3 ohms across the element connection last night and that is supposed to be in the wheel house of 8 to 25 ohms? although on the low side!
sorry i just did it again and you are right, one leg is 1.0 something volts
not getting voltage to both legs........ what now
this is the first time i have done something online like this, it has been cool so far!
you got me thinking when i got 110 v on each leg at element i had it connected stil so i have been back tracking s we were talking.\
just checked plug at wall 110 on one side to ground and 40 volts on other.
same at breaker in panel........ do i have a bad breaker on one leg?
i reset breaker at beginning of problem to make sure it wasn't tripped.
as i back tracked i just checked from ground to each screw on the breaker and that was what i seen on meter 110 on one leg and 40 on the other
i just check the buss on each leg and 120 both side in panel and havn't lost anything else in house so i;m assuming breaker it self is bad .........does that make sense?
also i want to make sure i do the apyment thing correct , where is this but to pay you
and thank you in adavance for your assitance
please let me know if i'm assuming correctly
and again thanks