Appliance Repair Questions? Ask a Technician for Answers ASAP
Check the condenser coil to see if there's a layer of dust blocking the air flow through it. If there is vacuum it off, and give the unit an hour or so to return to normal operation.
If my answer helps you, please click on the 'accept' button. That's how we experts are paid for our efforts.
Hi. Welcome to JustAnswer.If the answer I provide for you is helpful, please click 'ACCEPT'. I won't be paid if you don't. Thank you.
Most likely the TVX is plugged. You should see fluxuations in your guages as the unit cycles. On both sides.
If the guages (especially on the low side) do not fluctuate then the expansion valve is plugged and will have to be replaced.
I just replaced it, along with the drier. evac. and charged doing same thing. the screen in the txv was clean.
the guage readings you provided was what swayed me towards the valve.
Glad you got it fixed.